You can never have too much power protection
Yes, ground fault circuit interrupters are a nuisance at times, but they
are there to keep you safe from 120 VAC power. These devices are
required wherever there is water near electrical circuits, such as in
kitchens, bathrooms, garages and on outside outlets.
A man recently was killed while standing in water, holding an electric
drill at a lake dock. There was a short between the metal case of the
drill and its power cord. He was electrocuted instantly. That could have
been avoided if the drill was plugged into a GFCI-protected outlet. A
small amount of current to ground would have shut off the GFCI breaker
and saved the man’s life.
The same applies on my service bench. I get an occasional GFCI trip, but
it is a minor inconvenience when the result could have been injury or
death. It also tells me when I have a piece of equipment that has
leakage to ground and should be worked on before it goes into service.
A power cord’s third wire is a safety ground that goes to the equipment
chassis. Yes, there are devices today that have two-wire power cords.
Look for a UL sticker, showing the equipment has been tested by United
Laboratories and is deemed safe to use.
Check equipment at your stations. If you find a two-wire powered device
without a sticker, replace the equipment or consider modifying it by
replacing the power cord with one that has three conductors. That third
wire, the ground, needs to be connected reliably to the equipment case.
Years ago there were no ground wires. It was normal on occasion to get a
tingle from a radio receiver with leakage to its chassis. You are in
greater danger today of being shocked, or even electrocuted, from one of
those older devices. A power transformer can develop a short from a
winding to its core. That could put a full 120 VAC on the metal case.
A three-wire power cord does you no good if it is plugged into
a three-wire to two-wire cheater/adapter, as shown in Fig. 1. Adapters
of that sort will defeat the ground connection and can create a
Every piece of equipment should be protected from over current.
Some older devices do not have fuses or circuit breakers. Again, you
should consider replacing any equipment that is a safety hazard.
Some engineers will drill a hole in a chassis and install a fuse holder
in the hot side of the incoming power cable. Others will use an inline
fuse, inside the chassis, to do the same thing to solve this safety
hazard problem. Note that insurance companies check for those things
when examining a damage claim.
Fig. 1: Don’t use a cheater adapter, like the one shown here.
It may not be legal in all locations, but I like to move
uninterruptible power supply batteries to the outside of a UPS unit to
keep them cool. Some UPS manufacturers offer boxes and cables for
external batteries. My experience is that batteries fail more
quickly when they are kept in the warm/hot environment of the inside of
a UPS unit.
Fig. 2: UPS batteries kept outside the UPS.
Fig. 2 shows the one at my place. The photo shows only see the back of
this rack-mounted 3000 watt APC brand UPS. On the batteries are a
permanently attached inexpensive voltmeter and documentation showing
what date the batteries were installed, along with the normal voltage.
As the only UPS in the facility, it runs seven computers, a security
system, smoke alarms, the internet connection and a phone system. The
UPS only needs to run for the 10 seconds required for the automatic
backup power generator to come online, plus 10 seconds or so for the UPS
to deem the power safe before switching back during a power outage. It
is a good and seamless system.
The grey PVC box, to the right, handles 120 VAC going to and from the
UPS. Wiring is arranged with plugs and jacks so the UPS can be easily
bypassed if it fails.
The output wiring of this UPS ties to a standard Square D QO
series load center with circuit breakers for all the UPS supported
Fig. 3: A surge arrester in a circuit breaker panel.
Added to it, and all other load centers in the facility, are Square D
QO2175SB Surgebreakers (a trademark name of Schneider Electric) that
plug in like standard circuit breakers. This product is the size of a
two-pole circuit breaker, but without a breaker handle. A green light
indicates all is well. Its job is to shave voltage spikes from lightning
strikes and power surges. The Surgebreaker is even, as I understand it,
capable of drawing enough current to trip the main breaker in the box
and thus protect the connected equipment. Likely other
manufacturers have similar products. Every circuit breaker panel should
have one. You can never have too much power protection!
In this case, all UPS supported power is sent to orange 120 VAC
receptacles labeled “UPS loads only.”
Remember, a load too large for any UPS will bring down the entire
system. I’ve seen it at radio stations. Just because there is an
available power outlet doesn’t mean anything can be plugged in.
You should use electrical outlet safety caps to keep people from
inserting a power plug where it shouldn’t be. Covers often come in 12
packs for about $2 (Leviton 12777 or equivalent) at hardware and
department stores. You can use any extra covers to help keep electrical
outlets safe from kids at your home.
Fig. 4: Safety covers are used to protect power outlets.
Repairing older equipment often requires replacing incandescent
indicator lamps. I often use a resistor in series with lamps to lower
the voltage and extend lamp life. In fact, 10 percent less voltage will
double its life. So what value resistor is right?
We start by knowing the resistance of the lamp. Using an ohmmeter
to measure a lamp will not reveal a correct answer. Resistance changes
as the lamp heats up. My recent article (“Ohm’s
Law Answers Your Questions”) shows a way to figure it out.
If the lamp is a #47, it is rated at 6.3 volts and draws 0.15 amperes of
current. To find its resistance, divide 6.3 volts by 0.15 amperes. The
answer is 42 ohms. Adding a resistor of one-tenth that value in series
will result in about a 10 percent reduction in voltage at the lamp. A
4.7 ohm resistor is the nearest standard value and is close enough. Now
the lamp runs at 5.67 volts and is almost as bright as it was at 6.3
volts. The other important resistor rating is its power dissipation
capability. Ohm’s Law tells us that just under 0.1 watt will be lost to
heat in the resistor. Use at least a 1/2 watt resistor because it will
be dissipating power/generating heat whenever the light is on. More
resistor wattage capability is better in this case.
There are replacement LED lamps that are direct drop-in replacements
today. On the other side of the coin, incandescent lamps will run the
same on AC or DC power. LEDs want DC at about 2 volts. Use a series
resistor to keep current within LED specifications. I typically like to
see LED indicators run with 10 m.a. of current. You can use them on AC
if you don’t exceed their maximum allowed reverse voltage specification,
which could be as low as 5 volts. A #47 lamp might cost less than $1
while its LED drop-in replacement, with built-in resistor or other
electronics, could be $7.
DO IT SAFELY
It is up to you to use good judgment when modifying equipment.
If you are unsure of how to get the right results and/or your
capabilities in doing it well, then have an experienced tech do the
work. It makes perfect sense.
Mark Persons, ham W0MH, is an SBE Certified Professional Broadcast
Engineer and SBE Engineer of the Year in 2018. He is now retired after
more than 40 years in business. His website is www.mwpersons.com.
This is a reprint of the article which appeared in the online
version of Radio World at:
Comment on this or any article.
Write to email@example.com.